SPECIFICATIONS & STANDARDS
ICEA S-75-381/NEMA WC58, ASTM B 172, ASTM B 33
Conductors: Flexible strand tinned copper conductor, ASTM B-172 and ICEA S-75-381, table 3-22.
Conductor Shield: Extruded semi-conducting layer over conductor. ICEA S-75-381 sec. 3.14.
Insulation: Ethylene-propylene rubber (EPR) ICEA S-75-381, table 3-22.
Insulation Shield: Semi-conducting bedding tape and composite tinned copper/polyamide braid 60% minimum coverage.
Color Code: Polyamide braid color code - black, white, red, ICEA S-75-381.
Grounding Cond: Tinned copper - ICEA S-75-381 Tab. 3-25.
Ground Check: Yellow polypropylene-insulated tinned copper conductor, ICEA S-75-381 Tab. 3-22
Cable Assembly: Three power conductors, ground check and two non-insulated grounding conductors cabled together to form a round cable core.
Separator: Single faced rubber-filled binder tape applied over core.
Jacket: Black, extra heavy duty, high torsion-resistant, integral-filled, reinforced Neoprene thermoset jacket, ICEA S-75-381 Tab. 3-3, 3-22, Sec. 3.21.